Question: What setpoint should I set my differential pressure switch to for indicating when my filter is dirty?
Question: I am trying to measure building pressure relative to outside air pressure. However, in doing so, I am seeing fluctuations in the differential pressure readings. Is there any way to minimize or eliminate these fluctuations? Continue reading “Ask the Expert – Issues with Referencing Outside Air Pressure”
Dwyer Instruments, Inc. offers many types of flow measuring products including orifice plates, which are used as a flow sensing element with a differential pressure monitor.
Orifice plates are a primary flow element, detecting the flow of a fluid passing through the plate by sensing the pressure drop across the plate. When a fluid flows through a restriction in a pipe, it creates a pressure difference between upstream and downstream of the restriction. This pressure difference is proportional to flow rate according to Bernoulli’s principal, similar to a Pitot tube. Orifice plates are commonly used as they are simple to use, low cost, work with gases or liquids, and require low maintenance. Adversely, they do have large pressure losses with about 50% of the pressure drop not recoverable. Continue reading “Flow Measurement with Orifice Plates”
Dwyer Instruments, Inc. offers many temperature measuring products that use bimetal sensors as the sensing element.
Bimetal Thermometers measure temperature based on the differences in thermal expansion properties of metals. Pieces of metals with different thermal expansion coefficients are attached to each other in an assembly.
As the temperature applied to the metal sensor assembly increases, the metal strip with the larger temperature coefficient of expansion expands more. Continue reading “Bimetal Thermometers”
Understanding the necessary requirements for your product’s enclosure ratings is important, particularly when looking to gain the optimum life from your product while avoiding any safety concerns. Included below is a straight forward easy to understand overview of enclosure ratings, including NEMA types, IP ratings, and the difference between the two. We will be looking at these two common standards for industrial enclosures, what they equate to, some alternatives, and how to best choose the right one for your application. Continue reading “Weatherproof Enclosure Ratings: Speaking the Secret Language of NEMA and IP”