Dwyer Instruments, Inc. offers many air velocity measuring products that use thermal or hot-wire sensors as the sensing element. There are fixed duct mount styles for continuous monitoring, such as the Air Velocity Transmitters, Series 641, and portable insertion styles for testing, such as the Thermo-Anemometer Test Instrument, Model 471B and the Thermo-Anemometer Probe, Series AP2.
The objective for this writing is to inform HVAC technicians and contractors about the limitations of testing equipment currently used for testing, adjusting, and balancing HVAC systems. The need for more accurate instruments is immediate as energy programs are moving toward net-zero energy building efficiencies.
In doing so, HVAC technicians and contractors will struggle with tighter specifications as they tune HVAC systems with instruments that fail to provide the required accuracy and versatility. Continue reading “Advances in HVAC Test Equipment: The Importance of Diffuser Calibration for Flow Hood Measurements”
Methods of Air Balancing
Air balancing a distribution system is needed to properly direct the air flow in order to optimize the system’s design. Flow rates are tested, adjusted, and balanced as cubic feet per minute (CFM) or cubic meters per hour (m3/h). There are two traditional methods for balancing airflow at the terminals. The first is sequential balancing, which involves setting the zone and branch dampers in sequence. However, the most common method of air balancing is called proportional balancing.
- Standard air flow hoods do not correct for diffuser type when balancing a system.
- Proportional balancing is extremely difficult when a mixture of diffusers are present, due to the inaccuracy of standard hoods on slot diffusers.
- Below is a sample of diffusers tested on Dwyer’s Precision Air Calibration Station (Figure A) with a standard air flow hood followed by the Dwyer SMART Air Hood™ Balancing Instrument (Series SAH).
Figure A: Precision Air Hood Calibration Station
Continue reading “Balancing a HVAC System with Multiple Diffuser Types”
Dwyer Instruments offers many styles of Pitot tubes, which are a commonly used sensor for monitoring air velocity and flow rate in heating, ventilation, and air conditioning.
Pitot tubes are based on Bernoulli’s equation, which states an increase in the speed of a fluid occurs simultaneously with an increase in dynamic pressure and a decrease in static pressure. Pitot Tubes sense the dynamic pressure of the fluid flow at a particular point and were invented by French Engineer Henri Pitot in the early 18th century.