Understanding the necessary requirements for your product’s enclosure ratings is important, particularly when looking to gain the optimum life from your product while avoiding any safety concerns. Included below is a straight forward easy to understand overview of enclosure ratings, including NEMA types, IP ratings, and the difference between the two. We will be looking at these two common standards for industrial enclosures, what they equate to, some alternatives, and how to best choose the right one for your application. Continue reading “Weatherproof Enclosure Ratings: Speaking the Secret Language of NEMA and IP”
Question: Can the Flotect® Vane-Operated Flow Switch, Series V4, be installed in a vertical pipe run?
Question: I am looking to use a flowmeter calibrated for air to monitor CO2 flow. Are there any concerns or correction factors I need to apply?
A common flow measuring application is using a Magnehelic® Differential Pressure Gage with a Pitot Tube to measure velocity pressure. This velocity pressure can then be easily converted into velocity or flow rate. Continue reading “Custom Scales for Differential Pressure Gages”
Control valves are used to change process conditions such as flow, temperature, level, and pH. A complete control system would include: a sensor, controller, positioner or current to pressure transducer, and control valve. Globe valves, such as the Dwyer Series 2000VA/ 3000WA Hi-Flow™ Control Valve, are a very common type of control valve.
The Dwyer Hi-Flow™ Series control valves have pneumatic actuators that modulate the valve for flow control. The opening, closing and throttling of the valve plug is accomplished by varying the air pressure to the diaphragm in the actuator. Typically the control pressure signal is 3 to 15 psig. There are two types of actuators: Air-To-Lower and Air-To- Raise. Continue reading “Control Valve Actuator Sizing and Valve Action Selection”