The Dwyer SMART Air Hood® Balancing Instrument now has a TABopts Software option to make a great user experience even better.
The software by Ameritech Data Solutions presented with the HVAC air flow hood was unveiled at the 2018 AHR Expo.
How does a revolutionary and multi-award winning HVAC product become even more valuable to customers and the marketplace? Dwyer found a way to provide greater capabilities. Continue reading “TABopts Software for the Award Winning SMART Air Hood® Balancing Instrument”
Dwyer Instruments, Inc. was recognized for excellence in product design in the 14th annual Dealer Design Awards Program sponsored by The Air Conditioning Heating & Refrigeration News Magazine (The ACHR News). An independent panel of contractors acted as judges in the contest that had 81 entries. Three Dwyer products stole the spotlight this year: the PredictAir™ Application Software; the Series AVUL, Air Velocity Transmitter; and the Series 490A-HKIT, Hydronic Differential Pressure Manometer. ACHR News is the leading trade magazine in the heating, ventilating, air conditioning, and refrigeration industries.
Continue reading “Dwyer Recognized for HVACR Product Excellence”
The objective for this writing is to inform HVAC technicians and contractors about the limitations of testing equipment currently used for testing, adjusting, and balancing HVAC systems. The need for more accurate instruments is immediate as energy programs are moving toward net-zero energy building efficiencies.
In doing so, HVAC technicians and contractors will struggle with tighter specifications as they tune HVAC systems with instruments that fail to provide the required accuracy and versatility. Continue reading “Advances in HVAC Test Equipment: The Importance of Diffuser Calibration for Flow Hood Measurements”
Methods of Air Balancing
Air balancing a distribution system is needed to properly direct the air flow in order to optimize the system’s design. Flow rates are tested, adjusted, and balanced as cubic feet per minute (CFM) or cubic meters per hour (m3/h). There are two traditional methods for balancing airflow at the terminals. The first is sequential balancing, which involves setting the zone and branch dampers in sequence. However, the most common method of air balancing is called proportional balancing.
Continue reading “Air Balancing HVAC Systems”
- Standard air flow hoods do not correct for diffuser type when balancing a system.
- Proportional balancing is extremely difficult when a mixture of diffusers are present, due to the inaccuracy of standard hoods on slot diffusers.
- Below is a sample of diffusers tested on Dwyer’s Precision Air Calibration Station (Figure A) with a standard air flow hood followed by the Dwyer SMART Air Hood™ Balancing Instrument (Series SAH).
Figure A: Precision Air Hood Calibration Station
Continue reading “Balancing a HVAC System with Multiple Diffuser Types”