Question: Is there a kit I can buy with the Magnehelic® Differential Pressure Gage for monitoring air filters, so that I don’t have to buy all the tubing, static pressure tips, and a bracket separately?
Dwyer offers several carbon dioxide measuring products that use non-dispersive infrared sensors as the sensing element. Carbon dioxide sensors are commonly used in building automation systems to monitor air quality. The level of carbon dioxide is indirectly proportional to the amount of people in a space and can be used to adjust ventilation for the space.
There are two basic types of gas sensing technologies: chemical reaction and infrared spectroscopic. Most chemical reaction sensors are electrochemical sensors, which are not as reliable as they can interact with multiple gases and wear from interaction with the gas. Continue reading “Non-Dispersive Infrared (NDIR) Carbon Dioxide Sensors”
There are several reasons why a 38R is a great choice in your heating or cooling applications, with the most obvious being that there is no power required. The 38R temperature regulator is a fully self-contained unit, requiring no external power source. This could mean substantial savings over the operation of other types of valves.
Regulation takes place when the sensing bulb is exposed to changes in temperature. The thermal system is charged with a predetermined amount of vapor fill, which, when heated, will cause a bellows within the unit’s actuator housing to expand. As the bellows expands, it compresses a return spring while simultaneously moving the valve stem downward to stroke the valve.
When the process temperature decreases or in the event of thermal system failure, the return spring will move the valve stem upward to the “out” position. Continue reading “Why Choose a 38R Self-Acting Control Valve?”
Several applications require manual reset switches, which are switches that need to be physically reset by an individual for a process to continue or restart. A manual reset is often needed when an area has to be inspected prior to equipment restart. This can help to ensure the safety/inspection of both equipment and other individuals in the area.
Some switches have a mechanical manual reset (such as the Dwyer Series 1900, 1831, and 1800). However, there may be a need to have a manual reset for applications beyond what these switches are designed for. If a pump is allowed to run with a clogged filter, for example, this may severely damage the pump. Continue reading “How to Program a Switch for Manual Reset”
A daisy chain is a wiring strategy where multiple devices are wired together in sequence. This is similar to the way in which flowers can be linked together to form chains or rings, using flower stems as a chain to connect each flower to one another.
In this example, a pressure transmitting cell is the “daisy” and a circuit loop is the “chain.” Continue reading “The Basics of Daisy Chaining”